Dimmer switch issues
Hey all -
I've just replaced a new light fixture (from a previously existing light fixture) that used to use a pull chain switch to turn it on and off.
Well, my girlfriend wanted a switch for the light instead of the pull switch so I ran new lines to the switch. Everything worked out perfect - the light was safely installed, the switch turned the light on and off, lines were run properly etc etc etc., until she wanted a dimmer on that light. It's a chandelier that has 3 lights (60W each light x 3 = 180 total watts).
When I went to install the dimmer, for some reason, the lights kept "jumping" like the voltage was off or something. I've attached a diagram of the current setup.
In the drawing, you can see that I've run the lines from both the switch and the light to a junction box in the attic. The dimmer switch is on a single pole box so I'm trying to figure out how the single pole switch works just fine, but when I interchange it with a dimmer switch, it gets screwy!
Thanks in advance and for reading!
EDIT: Due to the OVERWHELMING responses from you people - fortunately I've figured this out on my own. So I suppose I can say thanks for nothing? :)
|All times are GMT -5. The time now is 12:33 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.