detached building subpanel 3-wire questions
first, what constitutes a "detached" building? my garage (and a small guest apt) is physically attached via a breezeway of nearly 20'. is it, by NEC definition, a detached or an attached building?
the garage has a subpanel fed by a 3-wire cable (2 hot, 1 gnd) which, in turn, is connected to the main subpanel in the house. from the discussion in a previous thread this seems to be legal prior to the 2008 NEC *if* the garage is a detached structure. however, i question the fact that the gnd of the cable is connected at the main subpanel rather than at the main panel itself. i think it should be ok but what say you?
fwiw, the house was build in the late '50s. thanks
It's an attached garage; you run the calbes through the breezeway roofed ceiling.
|All times are GMT -5. The time now is 12:46 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.