I'm running 4 #6 wires for a sub panel under ground about 90' the panel will be 60 amps i want to use pvc but need to know the right size to get to hold all this. There will be 2 90s and a pull box on each end.
1" PVC would work.
Just so you know, you can run a #10 ground for this. It does not need to be #6.
Also, why the pull boxes?
|All times are GMT -5. The time now is 09:44 PM.|