Connecting Conduit to Outdoor Load Center
As part of rewiring my house, I'm looking at connecting some new circuits to my outdoor load center. After doing some research, I believe I have a good idea of what's required. Still, some of the information has been sparse so I was hoping that I could get some confirmation that I'm on the right track.
Since the enclosure is metal, I've read recommendations to use threaded adapters on all PVC conduit (as opposed to box adapters). Thus I believe that there are three different sets of requirements depending on where the conduit connects.
1) Connections going into the top of the enclosure:
- A hub should be used with RMC or IMC (but cannot be used with EMT or PVC)
- A liquid tight connector can be used with EMT or PVC
- Avoiding unnecessary top connections is recommended.
2) Connections going into the sides of the enclosure at or above exposed conductors in the enclosure (such as the bus bar and ground/neutral bars)
- Can use a connector listed as rain/liquid tight
- This connection can also be made by using a bushing and lock nut on the inside, while using a gasket/sealing washer between the enclosure and the lock nut on the outside. A sealing lock nut can also be used instead of a separate gasket and lock nut on the outside.
3) Connections going into the sides below exposed conductors or into the bottom of the panel
- Simply need a bushing and lock nut on the inside, and a lock nut on the outside.
- Does this look correct?
- Is the outside lock nut needed when using PVC male adapters?
SD515, thanks for the corrections.
Regarding the "box adapter", I was referring to this thing:
I'm assuming that this is meant to be used when going into plastic boxes. The small portion is the same diameter as the PVC pipe, and the shoulder is a bit bigger than the associated knockout hole. So I believe that the intention is to put the box adapter through the knockout. And then attach PVC via either the built in hub or with a coupling.
With the hubs, I had found some folks talking about how most hubs were listed for RMC & IMC, but not EMT or PVC. But I should have guessed that adapters were available to make it work.
|All times are GMT -5. The time now is 05:10 PM.|