DIY Chatroom Home Improvement Forum (http://www.diychatroom.com/)
-   Electrical (http://www.diychatroom.com/f18/)
-   -   Connect a 14-2 to a 10-2 (http://www.diychatroom.com/f18/connect-14-2-10-2-a-160321/)

 Ncs0816 10-16-2012 07:33 PM

Connect a 14-2 to a 10-2

The gauges are so different. Should I solder them together or twist them together and cap them

 drwheels 10-16-2012 08:06 PM

If either was done you would limit yourself to a 15 amp breaker from using 14-2. 10-2 is usually on a 30 amp breaker and a fire hazard would result if 14-2 connected to it.

 darren 10-16-2012 08:09 PM

It is possible to twist them together but not the easy job if you have never done it. Strip lots of copper and try bending the #10 around the #14.

 joecaption 10-16-2012 08:47 PM

What is it your really trying to do?
I'd hate to see someone get hurt.

 Ncs0816 10-16-2012 09:08 PM

Quote:
 Originally Posted by joecaption (Post 1032314) What is it your really trying to do? I'd hate to see someone get hurt.
I'm tring to run 100 feet of 10-2 to a new outlet at the end of my driveway. The existing outlet had a 14-2 and will be using for power

 joecaption 10-16-2012 09:14 PM

Why 10-2? Seem a little over kill for just an outlet? What do you plan on powering?

 Ncs0816 10-16-2012 09:25 PM

Quote:
 Originally Posted by joecaption (Post 1032338) Why 10-2? Seem a little over kill for just an outlet? What do you plan on powering?
I'm using it. 10-2 will prevent more loss of volts. Correct?

 CheapCharlie 10-17-2012 10:32 AM

Sure, but the voltage drop depends on what load you have on the circuit. At only 100 feet I don't think you'd have to worry about it.

 Dave632 10-17-2012 10:50 AM

For a 100' run (200' total circuit length):
• #14 = 0.505 ohms
• #12 = 0.318 ohms
• #10 = 0.200 ohms
• (source)
Voltage drop, assuming a 15 Amp load (max for #14):
• #14 = ~7.5 volts
• #12 = ~4.8 volts
• #10 = ~3.0 volts
Whether the 4.5 volt difference is worth the extra cost and trouble of using #10 is up to you.

 CheapCharlie 10-17-2012 11:12 AM

Where are you from? If from Canada, the voltage drop is limited by code to 3% on a branch circuit.

 jbfan 10-17-2012 11:18 AM

Quote:
 Originally Posted by CheapCharlie (Post 1032604) Where are you from? If from Canada, the voltage drop is limited by code to 3% on a branch circuit.
It is just a recommendation in the states, not a code issue.

 CheapCharlie 10-17-2012 11:31 AM

That's why I posted that. Doesn't say in his profile

 Ncs0816 10-17-2012 05:36 PM

Quote:
 Originally Posted by Dave632 (Post 1032594) For a 100' run (200' total circuit length): #14 = 0.505 ohms #12 = 0.318 ohms #10 = 0.200 ohms (source) Voltage drop, assuming a 15 Amp load (max for #14): #14 = ~7.5 volts #12 = ~4.8 volts #10 = ~3.0 volts Whether the 4.5 volt difference is worth the extra cost and trouble of using #10 is up to you.
Is the total length 200?

 Ncs0816 10-17-2012 05:36 PM

Quote:
 Originally Posted by CheapCharlie (Post 1032614) That's why I posted that. Doesn't say in his profile
Live in virginia

 stickboy1375 10-17-2012 05:38 PM

12 Attachment(s)
Quote:
 Originally Posted by Ncs0816 (Post 1032269) The gauges are so different. Should I solder them together or twist them together and cap them
Just use wire nuts, align the ends and install wirenut.

All times are GMT -5. The time now is 08:29 PM.

vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.