Ceiling fan works, lights don't?
Explain more on how it's connected at the ceiling box.
From the fan/light there's typically a shared neutral/white and black for the fan hot and blue for the light hot. Have seen other wiring also but mostly blue/black. If the ceiling is constant hot or one switch operated both the fan and light leads connect to black at the box. If it's individually switched for fan and light to operate separately the fan and light lead would hook to separate hots at the box.
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.