Ceiling Fan and light switch conversion
Check the receptale that is switched.
The white wire going to the switch is connected to the black wire feeding the receptacle.
To make the receptacle hot all the time, pigtail a black wire to the incomong wire, and the black wire going to the switch.
The white wire from the switch now goes to the neutral of the receptacle.
The switch now has a hot and a neutral, but you still need to get a cable from the switch to the fan location.
Yes I am a Pirate, 200 years too late. "Jimmy Buffett"