


Thread Tools  Display Modes 
05252011, 03:40 PM  #1 
Member
Join Date: Jul 2009
Posts: 198
Rewards Points: 150

Calculations for voltage drop of wire
I was just talking with a design tech that I know and was comparing voltage drop data. I was surprised how far apart we were and it seems he uses a different method for the calculation. Mine seem to arrive at the same number as about any calculator online but his were up to 3X as much voltage drop.
Just curious what formula and tables references you use? Let's leave the actual application and and loads and such out of it and concentrate on the actual value. I would also like to know if you guys look mostly at 90c for service entrance wire or if you build for 75c? Thanks Advertisement 
05252011, 04:34 PM  #2 
Licensed electrician
Join Date: Sep 2007
Location: Maryland
Posts: 8,551
Rewards Points: 3,372

Calculations for voltage drop of wire
Were you using the total length of the circuit which is the out and back distance or only out? Were you using the same design load?
Your wire needs to be sized based on the lowest rated part of the system. You will not find terminations rated 90C, but the wire can be derated from the 90C ratings. Advertisement
__________________
Answers based on the National Electrical Code. Local amendments may apply. Check with your local building officials. 
05252011, 04:48 PM  #3 
Member
Join Date: Jul 2009
Posts: 198
Rewards Points: 150

Calculations for voltage drop of wire
Because of the length of run, wire heat is not as much an issue as Vdrop. Loads are being calculated phase  phase with equal Vdrop between them so of course it would double.
I am more or less looking for hard calculations here. As for the temp rating, I thought one could use a higher current rating but lower temp rating to offset operating higher temp wire? Is that not the case? Obviously the NEC will limit the current in the conductor to a safe level anyway and right now our wires are looking to run about 55C but Vdrop is a concern. I am working back through the physics of it and going to compare the NEC book to actual periodic table data just too see if there are engineered margins there. Sometimes too many compounded margins ends up getting ridiculous IMO. Last edited by viper; 05252011 at 04:51 PM. 
05252011, 06:57 PM  #4 
Lic Elect/Inspector/CPO
Join Date: Apr 2011
Location: NJ
Posts: 369
Rewards Points: 250

Calculations for voltage drop of wire
See 210.19 A1 FPN #4
The note says that the 3% is just for a branch circuit. For the Feeder and the Branch circuit its a total of 5% If you supply the information, I will do a calc and we could compare results. 
05252011, 07:35 PM  #5 
Member
Join Date: Jul 2009
Posts: 198
Rewards Points: 150

Calculations for voltage drop of wire
Thanks!
Example would be: 4/0 Aluminum 240V 1ph 500ft from transformer to load 150A load Another is 500mcm Al, 240V 1ph 500ft as well 300A load Oh, these would both be underground in conduit installations so I am figuring 1520C ambient. 
05252011, 07:50 PM  #6 
Member
Join Date: Nov 2007
Location: Nashua, NH, USA
Posts: 7,166
Rewards Points: 2,432

Calculations for voltage drop of wire
We do not use temperature when figuring voltage drop. However when choosing the wire size needed to avoid temperature problems (in conduit, in free air, kind of insulation, etc) we might already come up with a wire size large enough to not suffer excessive voltage drop.
__________________
(One morning on WRKO Radio) The tub's not clean! Let's remodel the bathroom. (One afternoon on WRKO Radio) It's time for an oil change. I'm going to trade in the car for next year's model. 
05252011, 07:54 PM  #7  
Sparky
Join Date: Mar 2011
Location: Central Florida
Posts: 705
Rewards Points: 508

Calculations for voltage drop of wireQuote:
#1 i get 15V(6.25%), to get under 5% i show needing 300kcmil AL, for 3% i show 500kcmil AL #2 i get 12.72V(5.3%)to get under 5% i show needing 600kcmil AL, for 3% i show 1 run of 900kcmil AL, 2 runs of 500kcmil AL, 3 runs of 300kcmil or 4 runs of 250kcmil AL 

05252011, 09:24 PM  #8 
Member
Join Date: Jul 2009
Posts: 198
Rewards Points: 150

Calculations for voltage drop of wire
Huh, that is yet another value. do you happen to have the equation that was used to calculate that?
One that seems to be floating around the net that I am not sure I agree with is (2*L*R*I)/1000 That produces 12.06% for the 4/0 using .0804/K for resistance. The NEC books I think is .1 ohms for 4/0 so there is a little discrepancy there. 
05252011, 09:39 PM  #9 
Member
Join Date: Apr 2011
Location: Almost Arkansas
Posts: 2,764
Rewards Points: 2,000

Calculations for voltage drop of wire
My turn....300 mcm copper....................500 mcm alum.

05252011, 10:19 PM  #10 
Sparky
Join Date: Mar 2011
Location: Central Florida
Posts: 705
Rewards Points: 508

Calculations for voltage drop of wire 
05262011, 05:49 AM  #11 
Lic Elect/Inspector/CPO
Join Date: Apr 2011
Location: NJ
Posts: 369
Rewards Points: 250

Calculations for voltage drop of wire
#1 500 kcm
#2 900 kcm 
05262011, 11:20 AM  #12 
Member
Join Date: Jun 2007
Posts: 3,566
Rewards Points: 2,120

Calculations for voltage drop of wire 
05262011, 04:07 PM  #13 
Member
Join Date: Apr 2011
Location: Almost Arkansas
Posts: 2,764
Rewards Points: 2,000

Calculations for voltage drop of wire
http://www.csgnetwork.com/wiresizecalc.html
I use this often. Advertisement 
Thread Tools  
Display Modes  


Similar Threads  
Thread  Thread Starter  Forum  Replies  Last Post 
which GFCI to buy?  mike932  Electrical  138  05152011 04:38 PM 
Box fill and wire nuts  zephed666  Electrical  7  05022011 12:51 PM 
Outlet With Swith and Older (White, Black, Red) Wire  CaptChaos  Electrical  18  09142009 11:17 PM 
New Stove, old wires  2 wire vs 3 wire  DIYGST  Electrical  22  03022009 04:13 PM 
hooking up dryer....bronx ny code  SURFBUG  Appliances  6  10142008 09:41 PM 