Calculating "load" - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Calculating "load"
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

11-30-2007, 12:06 PM   #1
Newbie

Join Date: Nov 2007
Posts: 3
Rewards Points: 10

Hello, new guy here.
I have questions regarding how many lines I need to my breaker, wire gauge etc.

Here's what I need to do:
This is for my basement. I have a room where I have 12 x 35W halogen potlights. Also run 2 computers, scanner, fax, various other misc. electrical devices. An airbrush spraybooth, TV, and a couple other floor lamps. All in 1 room (approx. 15'x35').
My question, is there a way to calculate the gauge of wire I need to use and breakers etc. I have some open spots on my breaker, and I have an unused 2x15amp breaker switch for using 1 slot on the breaker (sorry if the terminology is way out of whack).

I've hooked up some lines previously so am somewhate familiar with this stuff.

11-30-2007, 07:07 PM   #2
Member

Join Date: Mar 2005
Location: Welland, Ontario
Posts: 12,586
Rewards Points: 11,964
Blog Entries: 11

15 amp breakers use 14 gauge wire and 20 amp circuit use 12 gauge wire. Unless you have a extra long cable run there is no need to calculate anything regarding wire size.
The calculation you need is called a load calculation.

 11-30-2007, 09:00 PM #3 UAW SKILLED TRADES     Join Date: Jan 2007 Location: Kansas Posts: 5,341 Rewards Points: 2,652 Most likely if you put your lighting loads a 15 amp breaker and your cord and plug stuff on general purpose 20 amp branch circuit(s) you will be fine. 15 amp breaker = 14 awg copper wire 20 amp breaker = 12 awg copper wire. Use 5-15r receptacles like these below for 15 amp circuits or 20 amp circuits the 5-20r is not required on a 20 amp branch circuit that serves more than one receptacle in the USA .....if in Canada I believe you must use 20 amp receptacles on 20 amp circuits and 15 amp receptacles on 15 amp circuits. 15 amp (5-15R) ... 20 amp ( 5-20R) In the Usa and Canada.... A 15 amp branch circuit protected by a 15 amp circuit breaker will give you 1800 watts of power A 20 amp branch circuit will give you 2400 watts of power. It's becoming common to put entertainment equipment on its own 20 amp branch circuit. Example.... You have 12 x 35watts = 420 watts... so you still have 1380 watts of power left on a 15 amp branch circuit. The idea here is if you approach 1800 watts of connected load and that load is all going to frequently be on at the same time then you need to design your circuits appropriately so you don't overload them. It is becoming more common for entertainment systems to require dedicated branch circuits because of the total load requirements. Anyway generally speaking lights on 15 and receptacles on 20 and you are usually fine. Last edited by Stubbie; 11-30-2007 at 09:07 PM.

 11-30-2007, 10:02 PM #4 Electrician philosopher   Join Date: Aug 2007 Location: Lilburn, GA Posts: 838 Rewards Points: 500 I'm curious about the airbrush spraybooth. How many watts is that? I often run a seperate circuit for computers (20A) if it is in the budget. And what Stubbie said. Andy

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post purplejay General DIY Discussions 1 05-20-2008 12:19 PM suprashy Electrical 6 09-16-2007 05:37 PM wbjdmd Electrical 18 11-01-2006 06:18 PM

Top of Page | View New Posts