Lightning struck my house and I have a 60a fpe breaker in my Box that goed to the Spa 60a gfi outside. There is also a single 30a 115v in that box. Ever since the storm the 60a in my main panel will set and trip after a minute or so. Even when I isolate it from every connected to it, it still trips. I tried changing it but no luck. I do get a small reading from ground to one hot leg. BUT every thing goes on when I reset the breaker for a minute or a little more. Like I said I ioslated it and disconnected everything going thought the line. It still trips. I am Totally lost at what else to try. Any help would be much appreciated. Thanks
Bad breaker, most likely. FPE, good luck finding a replacement. Some electricians will not even do any work whatsoever on FPE panels due to the liability involved.
I know you can find FPE replacements, but you are taking your chances, IMHO.
You may be looking at a replacement panel.
I'm not trying to scare you are anything, but FPE panels/breakers have a bad rep for a reason.
|All times are GMT -5. The time now is 06:26 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.