Box Fill Conductor Count - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Box fill conductor count
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

06-28-2007, 04:06 AM   #1
Newbie

Join Date: Jun 2007
Location: San Bernardino, Calif.
Posts: 8
Rewards Points: 10

## Box fill conductor count

For box-fill calculations, in a junction box, if I splice an incoming conductor to an outgoing conductor, do I now have two conductors or one?

06-28-2007, 07:10 AM   #2

Join Date: Feb 2004
Location: NY State
Posts: 7,737
Rewards Points: 1,824

It's confusing, but clear if you read it closely:

(1) Conductor Fill
Each conductor that originates outside the box and terminates or is spliced within the box shall be counted once, and each conductor that passes through the box without splice or termination shall be counted once. A looped, unbroken conductor not less than twice the minimum length required for free conductors in 300.14 shall be counted twice. The conductor fill shall be calculated using Table 314.16(B). A conductor, no part of which leaves the box, shall not be counted.

A wire ending in the box, be it spliced, capped, etc. Counts ONE.
A wire passing clean through the box, no loop or slack. Counts ONE.
A wire passing through the box, with enough slack to be cut and spliced. TWO conductors.

Your question would have two of the first example.

__________________
Sometimes I feel like if I answer any more questions it is like someone trying to climb over a fence to jump off a bridge and me giving them a boost.

 06-28-2007, 10:25 AM #3 Member   Join Date: Feb 2007 Location: Marietta, GA Posts: 209 Rewards Points: 150 Here's link that explains it as well. http://www.taunton.com/finehomebuild...ger-boxes.aspx __________________ It takes less time to do a thing right than it does to explain why you did it wrong. -Henry Wadsworth Longfellow
06-28-2007, 12:21 PM   #4
Newbie

Join Date: Jun 2007
Location: San Bernardino, Calif.
Posts: 8
Rewards Points: 10

Quote:
 Originally Posted by Speedy Petey It's confusing, but clear if you read it closely:
Yes, that is clear enough. I don't have a code book, and couldn't find a site that quoted it on this topic. Not that I spent a LOT of time looking . . . .

Thank you very much.

Last edited by Doug_Shaver; 06-28-2007 at 12:22 PM. Reason: Inadvertent deletion before posting.

06-28-2007, 12:35 PM   #5
Newbie

Join Date: Jun 2007
Location: San Bernardino, Calif.
Posts: 8
Rewards Points: 10

Quote:
 Originally Posted by beer_geek Here's link that explains it as well.
Thank you. I found that page during my research. From it, I inferred what the answer to my question probably was. But, since it assumed the installation of a receptacle, and the box in question won't have any devices, I wanted to double-check.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules