I have a switch box (2 switches) with a feed coming in. There are separate feeds going to the light and an exhaust fan. The prior electrician (termed used loosely) had three way switches on the fan and light. It was wired such that either the light would work of the fan would work but neither simultaneously. He also had the neutrals switched.
I need to rewire this
After isolating which hot and which neutral go to which device, how should I wire this with two switches that are independent? Do I need a jumper? I just can't seem to wrap my brain around the proper configuration.