basic code question
Originally Posted by deko
I need to install a single pole 120v switch in an interior wall. Is it acceptable to wall fish a single run of 14/2 NM cable to the switch using both black and white conductors as hot (with ground to the switch) and then tie it into a junction box in the attic?
If this is what you are referring to:
then it's fine.
(Diagram by DIYChatroom poster Stubbie, from his post # 11 here
Home Inspections, Infrared (Thermal Imaging) Leak Identification and Inspection Services, Roof, Attic, Building, Basement and Foundation Moisture Intrusion and Water Leak Inspections, Troubled Building Consultations - Serving Chicago and Suburbs
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.