I'm in an old 50s bungalow and want to add 6 new pot lights to an existing circuit. The circuit currently has 4 pot lights, two wall scones and two receptacle. I'm planning to take out the two wall scones since they are not tied to a light switch. In the end I'll have 10 pot lights and 2 receptacles.
10 pot lights @ 75watt each = 750watt = 6.25A
2 receptacle @ 2amp (??) each = 4A
The one light switch will turn on all 10 lights drawing 6.25amps.
Is it safe to keep the receptacles on the same circuit or do I need to run a new circuit just for the two receptacles. Just my vaccum cleaner already draws 10amps I believe. I guess I could vacuum in the dark
I can also use other receptacles to vaccum with but does anyone know what other appliances that will trip the breaker if I have a continuous load of 6.25 amps?
All responses based on the 2011 NEC.
If you live in New Jersey click here. All other states click here.
Please check with local, county and state officials as laws may vary.
Sizing motors here. Online motor calculator here. Online calculators here.