Basement Bathroom Circuit
Hello, just looking for some confirmation here. I have a sub-panel in my basement, and am using all 20 amp breakers & outlets and using Romex 12-2 for everything.
Given those assumptions, is it OK to wire the light & fan in the bathroom (assuming it's NOT directly over a bath/shower enclosure, but rather centered in bathroom and is NOT recessed) on the same circuit as outlets outside of the bathroom in other parts of the basement. Then, any outlets inside the bathroom will be on their own dedicated circuit and will first go through a GFCI receptacle. Does this sound like a correct setup? Would any other way be preferred for one reason or another?
My assumption is that no outlets in the basement can be connected to the same circuit as the GFI bathroom outlet circuit. So, I wanted to re-use the light/fan circuit for other basement outlets so that I'm not tying up 2 circuits just for the bathroom.
The lights can come from a different circuit. For an ordinary bathroom, the only requirement is that the bathroom have at least one 20A GFCI protected receptacle. The lights can be on the same circuit if you want, but then the circuit cannot leave the bathroom.
|All times are GMT -5. The time now is 10:55 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.