Baseboard Heater: Can I wire it to plug into an AC recepticle?
I've got a baseboard heater that I am not using in 1 room and I'd like to move it into another. However, instead of rewiring the room or purchasing a new space heater.....I thought I could just wire it to ac cord so that I can store it away in the fall, spring and summer.
I know that I will void the manufacture warranty, but I was wondering:
BTW- The outlet I want to plug into is 15 amp. Voltage.....not exactly sure. I would think 120, but my breaker isn't labled. Its only 1 switch, not a double switch (is that were 220 ie "2 20 amps" comes from?).
Here are the electrical details regarding my baseboard heater:
Model Number: 2F500-1A
Watts 120V: 500
Amps 120V: 4.17
Weight: 6 LBS
I know that this will seem like a drag but I think that voiding the warrenty on the heater wouldn't be prudent. Suppose something bad DOES happen and a fire starts. Insurance is not going to look kindly on a modified appliance that started it. Long story short, code says that if a device is not listed for a use, you can't use it. It's a small enough unit that a comparable one that IS listed wouldn't be hard to get. Hope that helps. Sorry for the bad news.
if this heater is not used anymore and it is on delcated circuit then a good chance you can used for the A/C but it will only work if the thermosat is on the heater itself but with wall thermoast it can be doable but if you no longer want the heater you have to remove the thermast and wirenutted them and put in blank cover but you can not bury the box ditto with the splices in the wall.
some case there is a asscorey kit you can add on to the baseboard heater like this [ you may have to scroll down a little then you get the idea with it ]
this will get you some idea with it but before you do it make sure if this heater is delcated circuit [ trust me you will understand why in a min ]
becaue the window shaker [ window mounted air conding] will useally take more than 7 amp of power easly
Secondly, I missed why it is important to have a dedicated circuit. If it is only drawing 4.17 amps....why can't it share a circuit with a hallway light and an outlet using a lamp/cd player?
|All times are GMT -5. The time now is 07:22 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved