Adding recessed lighting to an existing circuit
i have just installed 4 cans controlled by a dimmer switch using 14/2 wire and plan to hook into a 15A circuit. The easiest wire for me to hook into this circuit is on the load side of a receptacle that goes to another receptacle. can I cut the wire that goes between receptacles and split the hot wire so it goes to the new recessed cans ( same for the white wire) and then on to the receptacle as previous?
|All times are GMT -4. The time now is 09:14 AM.|
© 2003 - 2010 The Building Network LLC