Adding a Hot Receptacle to a 3-Way Switch
As my topic indicates i'm trying to wire a hot receptacle to a 3-way switch. The issue I am having with this is, I am trying to added it into the box with only the 14-3 wire going to it. Meaning the original power source is not in this box, it is in the other box of the 3 way switch.
Any help would be greatly appreciated.
You will need to find another soruce for the receptacle.
All you have in the box are switch legs and travelers.
You would need a neutral and a constant hot to work.
I agree. If you only have the three wire cable then you don't have a neutral wire for the receptacle. Find another source of power.
|All times are GMT -5. The time now is 08:07 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.