I am adding a 4 way switch to a 3 way sw system. I am going to put the the new 4 way switch where one of the existing 3 way switches is currently. I am running 3 conductor cable the the new location and then i am going to put the 3 way sw there. My question is i need to use all 3 wires as hot, how do i mark the white one ??