??? About Calculating Loads For A Sub Panel - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum ??? about calculating loads for a sub panel
 User Name Remember Me? Password
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

 Thread Tools Display Modes
12-03-2009, 01:58 PM   #1
Newbie

Join Date: Nov 2009
Location: Dora, Al
Posts: 3
Rewards Points: 10

## ??? about calculating loads for a sub panel

Hi guys (& gals), First post to the forum. I have what may be a really elementary question for you. I have run a couple of searches but have not found this answered yet.

Anyway, here goes. I am planning to install a sub panel to an outbuilding for a workshop. It will have both 220v & 110v circuits on it. When I calculate the max potential load I might draw on the (1) 220v circuit (say 24 amps) and the (4)110v circuits (say 54 amps total), do I halve the 110v total & add to the 220v total to get the max. ie 54/2 = 27 + 24 = 51 total amps @ 220v for the sub panel, so I could use a 60 amp breaker in the main box to supply the sub?

I've done basic wiring (lights, recepticles, switches), but only on 110v circuits and nothing that would have a heavy load. I've never had to account for 220 & 110 before when calculating loads.

Thanks for the help.

### Advertisement

12-03-2009, 02:33 PM   #2
Electrical Contractor

Join Date: Jun 2004
Location: Newnan GA
Posts: 7,026
Rewards Points: 648

How did you arrive at the figures you have listed?

### Advertisement

__________________
"The problem isn't that Hillary Clinton lies. We all know she lies. The problem is that her supporters don't seem to care"

 12-03-2009, 02:48 PM #3 Newbie   Join Date: Nov 2009 Location: Dora, Al Posts: 3 Rewards Points: 10 I imagined what could be a possible (if rare) situation like the following: A cold night in the shop: Lights, radio, heater, air compressor, shop vac, air cleaner, drawing a total of ~54 amps on the various 110v circuits along with a dust collector and table saw running on the 220v curcuit drawing a total of 24 amps. The numbers made up, I don't have the exact numbers in front of me. It was just to see if my method of calculation was correct for combining the total load for the combined 220 / 110 circuits.

 12-03-2009, 06:23 PM #4 Member   Join Date: Jan 2009 Location: South of Boston, MA Posts: 17,248 Rewards Points: 2,000 Sub panel will be a 240v sub, so all loads are calculated at 240v 54a @120v = 27a @ 240v Yes - sounds like a 60a sub would work if your loads are as described For a detached structure a 60a sub is the min to run There is a code section that requires a 60a disconnect as a min You will also need 2 grounds rods Some discussion going on another board as someone ran a 50a breaker in the Main to a 100a sub in the shed Inspector wants him to feed it with a 60a or remove the 100a sub & reduce it to a 30a & 2 circuits
 12-03-2009, 07:58 PM #5 Newbie   Join Date: Nov 2009 Location: Dora, Al Posts: 3 Rewards Points: 10 Thanks Scuba_Dave.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post philipjcaputo Electrical 1 10-30-2009 03:35 AM theatretch85 Electrical 5 09-20-2009 11:09 PM GuitarJack Electrical 7 08-25-2009 08:43 PM leonard_voet Electrical 19 04-09-2008 10:27 AM Nhrafan Electrical 6 04-01-2008 03:03 PM

Top of Page | View New Posts

 Terms of Use

Search Engine Friendly URLs by vBSEO 3.6.1