4-way Switch With Multiple End Of Run Lights - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum 4-way switch with multiple end of run lights
 User Name Remember Me? Password
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

 Thread Tools Display Modes
06-08-2012, 10:31 AM   #1
Newbie

Join Date: Mar 2010
Posts: 10
Rewards Points: 18

## 4-way switch with multiple end of run lights

Hi. I am seeing wiring diagrams with contradictory solutions to this question. Can someone please help?

I am wiring some hall lights as follows:

Line--> 3-way switch--> 4-way switch--> 3-way switch ====> Light ====> Light ====> Light ====> Light ====> Light.

So the question is, do I need 14/3 or 14/2 Romex running between the lights? (The = in this diagram.)

To me, this is just an extended switch loop, so my thinking is I should be able to use 14/2 (The amperage of the circuit is sufficient for 14 gauge on this load). Yet some diagrams show 14/3. Others show 14/2 between the lights.

Thanks a million. I am sitting here stumped, with holes in my wall.

06-08-2012, 10:39 AM   #2

Join Date: Sep 2007
Location: Maryland
Posts: 10,859
Rewards Points: 1,872

You only need xx-2 between the lights in that wiring setup. The xx-3 will need to be between the switches.

__________________
Answers based on the National Electrical Code. Local amendments may apply. Check with your local building officials.

 The Following User Says Thank You to Jim Port For This Useful Post: daviswhite (06-08-2012)
 06-08-2012, 11:39 AM #3 Member     Join Date: Mar 2005 Location: Welland, Ontario Posts: 13,456 Rewards Points: 13,712 Blog Entries: 11 14/2 is all you need. This is not a switch loop. If it was a switch loop you would need 14/3 and the switches would be at the opposite end of the circuit from the power feed.

06-08-2012, 12:34 PM   #4
Newbie

Join Date: Mar 2010
Posts: 10
Rewards Points: 18

## thanks, Joe

I was not precise with my language. That's why you guys are the pro's.

 06-08-2012, 12:52 PM #5 Member   Join Date: Oct 2011 Location: Ohio Posts: 2,780 Rewards Points: 2,516 Heres something that was put together for another question on 4-way. Each switch turns on all 11 can lights. Attached Thumbnails
06-08-2012, 01:46 PM   #6
Newbie

Join Date: Mar 2010
Posts: 10
Rewards Points: 18

## Thanks, Hammerlane and all

The common theme, from Hammerlane's diagram, etc., is that the string of lights, no matter where it is after the third switch, feed off the common of the third switch, and their lights' neutrals splice all the way back to the white/neutral of the line-in.

That way sounds so simple. I think I have it right.

This is a great site. Thanks, everyone! I'm moving again.

 Tags 4-way , electrical , wiring

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post RickSene Electrical 6 05-13-2017 04:29 PM naty0629 Electrical 14 05-18-2012 12:03 PM DIY Mark Electrical 1 12-03-2011 11:15 AM simplyphp Electrical 36 11-25-2010 02:47 PM mark_anderson_u Electrical 0 11-02-2010 09:06 AM

Top of Page | View New Posts