DIY Chatroom Home Improvement Forum (http://www.diychatroom.com/)
-   Electrical (http://www.diychatroom.com/f18/)
-   -   4-way switch with multiple end of run lights (http://www.diychatroom.com/f18/4-way-switch-multiple-end-run-lights-146416/)

 daviswhite 06-08-2012 10:31 AM

4-way switch with multiple end of run lights

I am wiring some hall lights as follows:

Line--> 3-way switch--> 4-way switch--> 3-way switch ====> Light ====> Light ====> Light ====> Light ====> Light.

So the question is, do I need 14/3 or 14/2 Romex running between the lights? (The = in this diagram.)

To me, this is just an extended switch loop, so my thinking is I should be able to use 14/2 (The amperage of the circuit is sufficient for 14 gauge on this load). Yet some diagrams show 14/3. Others show 14/2 between the lights.

Thanks a million. I am sitting here stumped, with holes in my wall.

 Jim Port 06-08-2012 10:39 AM

You only need xx-2 between the lights in that wiring setup. The xx-3 will need to be between the switches.

 joed 06-08-2012 11:39 AM

14/2 is all you need.
This is not a switch loop. If it was a switch loop you would need 14/3 and the switches would be at the opposite end of the circuit from the power feed.

 daviswhite 06-08-2012 12:34 PM

thanks, Joe

I was not precise with my language. That's why you guys are the pro's.

:yes:

 hammerlane 06-08-2012 12:52 PM

1 Attachment(s)
Heres something that was put together for another question on 4-way. Each switch turns on all 11 can lights.

 daviswhite 06-08-2012 01:46 PM

Thanks, Hammerlane and all

The common theme, from Hammerlane's diagram, etc., is that the string of lights, no matter where it is after the third switch, feed off the common of the third switch, and their lights' neutrals splice all the way back to the white/neutral of the line-in.

That way sounds so simple. I think I have it right.

This is a great site. Thanks, everyone! I'm moving again.

 All times are GMT -5. The time now is 12:03 AM.