Originally Posted by Jim Port
General purpose circuits are prohibited from being greater than 20 amp.
Yea, I was starting to get that feeling, especially with Dave's response.
I had previously wired up a two breaker sub-panel feed from a single pole 30 amp breaker with 10/2 wire. I also have an extra 10/2 wire that was used for an A/C circuit that was upgraded.
Now that I'm finishing in the basement, I've got to modify the sub-panel. The inspector wants 10/3.
It all means I'm going to have some extra 10/2 that I was looking for some "best" ways to use... looks like it's going to need to be used as over-sized 20 amp circuits.