3 way wiring
Hi, I want to wire my hall and landing lights so that both lights can be switched from either upstairs or downstairs, can someone give me an easy to understand diagram.
The wiring is the easy part as you can see from the diagram. The hard part is running the red wire known as the "traveler" from switch to switch. Good luck
There are several methods for 3way wiring, depending on what components are where.
Instructions to go with the above posted diagrams:
3 way switch wiring:
White from the source goes directly to the load.
Black from the source goes to the common terminal of one of the 3 way switches.
Black of the load goes to the common terminal of the other 3 way switch.
The travelers get hooked to the remaining terminals.
If you have to use a white as 'hot', it has to feed a switch and be taped black at both ends.
Use 14 gauge wire on a 15 amp circuit, 12 ga on a 20 amp circuit.
There are many different ways to wire 3 ways. Here is link to some of the more common.
|All times are GMT -5. The time now is 01:11 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.