Is there any way to wire up a light off of each switch in a 3-way switch setup? I have a light at the top of my stairs that comes off the top 3 way switch. The load comes into the bottom (of the stairs) 3 way switch. It works fine currently. However, there's not enough light. I want to add another light near the bottom of the stairs, and I can get a wire back to the bottom switch. Looking at it though, I don't see any way to wire that light in to the load switch though. Is there some way to do this that I'm not thinking of? Thanks,
If I understand, the hot reeds the top switch, and the load to the light comes from the bottom switch.
If this is correct, you may be able to add another light.
Tell us the wiring in each switch box and we can go from there.
__________________ "The problem isn't that Hillary Clinton lies. We all know she lies. The problem is that her supporters don't seem to care"