3 Way switches
This is the way my circuit looks. Except the switch on the bottom right I want to be a ganged box with another switch for a different light.. Do I have to run another common through since the common here is used as a Hot? The other common would be for the other light.
Yes you would need a neutral. The best thing to do is just pull another circuit in instead of somehow trying to rig this. Can you tap off of the hot and neutral wires in the first (left) box?
|All times are GMT -5. The time now is 04:29 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.