3 Phase Power Phase Question - Electrical - Page 2 - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum 3 phase power phase question
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

12-20-2008, 02:11 PM   #16
Member

Join Date: Jul 2008
Location: NW of D.C.
Posts: 5,990
Rewards Points: 2,000

Quote:
 Originally Posted by theatretch85 Search for "Phase Coupling", its done a lot with X10 systems in houses where there are multiple interfaces through out a house. http://kbase.x10.com/wiki/Phase_Coupling If you have an electric dryer outlet, this would be an easy install (also available in the 4pin variety as well) http://www.smarthome.com/4826B/Signa...epeater/p.aspx Though you would probably need two to couple between all three phases.
Your first link kind-of confirms that a large incand. lamp will help transferring the 121 kHz between phases.

A 400v bipolar capacitor should also do it. 1 µF at 60 Hz is 2650 Ω but at 121 kHz it's 1 Ω.

10 ea. of these
CAT# RMF-104
in parallel, from
http://www.allelectronics.com/
will set you back \$3.50.

I don't know what current they can handle, though. Capacitors have a ripple current rating, related to the heating they can tolerate due to ESR.

12-20-2008, 04:21 PM   #17
Member

Join Date: Nov 2007
Location: Nashua, NH, USA
Posts: 7,917
Rewards Points: 1,440

The capacitor's 400 volt rating means it can be put across lines with a 400 volt difference without burning out (actually less since you should have a safety factor built in). No problem connecting across two legs of a 3 phase household circuit, 208 volts. At 2650 ohms impedance for 60 Hz, it will draw about 80 milliamps or 16 watts.

Note that some capacitors, notably "electrolytic" capacitors, are meant for DC circuits. See the capacitor specs for the suitable kinds of power that the capacitor may be connected across.

You can design a "circuit" using coils and capacitors to bridge the phase legs that would have an even greater impedance at 60 Hz and still have a negligible impedance at the frequency used by your security equipment. The only disadvantage of the plain capacitor (let alone the incandescent lamp) is consumption of billable power.

__________________
The good conscientious technician or serviceperson will carry extra oils and lubricants in case the new pump did not come with oil or the oil was accidentally spilled, so the service call can be completed without an extra visit.

Last edited by AllanJ; 12-20-2008 at 04:36 PM.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post andrewmarcos@yahoo.co.uk Electrical 6 11-25-2008 11:07 AM Slocalaman Electrical 3 11-06-2008 04:23 PM Ronin_67 Electrical 2 08-08-2008 07:06 AM fburke Electrical 4 06-11-2008 04:56 PM curse21 Electrical 2 08-18-2004 11:17 PM

Top of Page | View New Posts