240/208 Heater wiring Question
I have a Dimplex single element heater with fan I am installing in a bathroom. It is the 208/240v model.
In looking at the diagram it does not make any reference to a neutral. It shows L1 and L2 and only mentions a neutral for the 120v modal and you would wire it to the L2 terminal.
I have ran a new 20A circuit using 12/3 romex. Do I need to hook the neutral to anything and just use the red black and ground? Should I just cap off the white??
I would think the motor for the fan would need it but that is rated for 240/208 also.
Thanks for any help
If it is a straight 208/240 then it would not need a neutral, just 2 hots and a ground. I would cap the white and not use it.
Thank you! that is exactly what i did and it works fine.
|All times are GMT -5. The time now is 10:06 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.