That is what I thought you 2 were talking about. And yes that is what exists, as I stated originally the 2 switches are on the 2 different phases (legs). I verifiied this by the positioning of the breakers in the panel (counting leg-A, leg-B, alternating back-and-forth as most panels alternate the legs to every other 1" space). I also verified this by measuring between the hot feeds for the two switches ( has 240 vac hot-to-hot, 120vac hot-to-neut). I just remember something about this in the 93 NEC stating if this configuration is used, it must be fed from a 2-pole breaker (so there won't be a live wire in the box if you should have one breaker off---this is exactly what I have!) Is this till the case or has this changed?