||06-17-2010 12:14 PM
york unit condensor
york unit condensor will not kick on by temp setting,? will run when contactors are pushed in by hand. what is wrong or could be?
||06-17-2010 07:32 PM
remove the stat off the subbase jump R to Y1 let somebody be out the window to tell you if it comes on then remove the jump..paper clip short piece of thin wire..just hold it there ...if it bumps on the stat in hand isn't making contact...take an pencil eraser clean all the contacts on the base and stat..see if fan runs in ON when switched....before cleaning to see if that is making contact...will check back..:whistling2:
|All times are GMT -5. The time now is 12:41 AM.
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved