well I had an hvac repair man come out today and he did say that it was low on freon and added two pounds to the system. He also spotted a leak in one of the pipes leading into the heat pump itself. He tightened the bolt and the leak stopped.
We also rechecked the drain pipe and made sure it wasn't clogged, as well as checked the drain pan for any holes and or leaks none was found. However we started the system again and it is still leaking water. I am going to try and clean the condensor again and see what happens but i'm not optimistic at this point.
Originally Posted by timthetoolman
Now im not a hvac tech...but i think i may be correct in saying the problem you are having with frost building on the coils is due the system needing to be charged? (Low on refridgerant?)