Wireless Thermostat Selection
Just had my 1st bi-annual furnace check-up. I have a Carrier Infinity 80 Mid - effic., installed 2 years ago.
I have a 1972 Semi-detached home, basement [has a bedroom and my office - I work out of weekdays] and main level and upper storey [1800 sq. ft.]. It has an energy efficiency rating af about 60%.
The service man who owns this 25 yr. old company says that when they put my Carrier in, the thermostat [wired] only had 2 wires connecting it, so it wasn't utilizing the 2-stage nature of this furnace. To use the 2-stage fan I need 4 wires [grrrr]! So he says my options are:
You do not need extra wires to use it as a 2 stage furnace. It is using a timed on algorithm to determine when to switch to high fire. Read about adaptive timing in this manual:
Most people cannot tell the difference from a 1 to 2 stage tstat with that furnace if I did a blind side by each test of the 2 types of stats after it has run a dozen cycles.
|All times are GMT -5. The time now is 05:09 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.