Will a 4T Evap. Coil w/50' Lineset suck in 21 oz R22 at 500 microns?
I'm getting pretty close to completing my 4T air handler/HP installation.
Final steps will be to connect the lineset, pressurize with N2, leak test, evac. to <500 microns and charge.
I need to add exactly 21 oz of R22 to account for my 50' lineset. (factory charge assumes 15' and they say to add .6 oz/ft over 15').
I'm just curious if all 21 oz will be sucked in while the lineset/evap. coil has been brought to 500 microns of vacuum. (ie Will this level of vacuum be enough to bring in all 21 oz. or will I need to fire up the unit and use the suction port to bring in any remaining charge?)
(I do have an accurate digital scale)
Yes . just make sure the r-22 is stored in room temp. if its cold out side/in the van. a cold r-22 can will have less pressure.
|All times are GMT -5. The time now is 06:37 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.