Why won't furnace restart?
Does the condensate pump have an extra overflow switch connected to 2 wires besides the main wiring. The switch is on the pump and if it is stuck open (thinks there is a high water level issue) then it stops 24 volts to the furnace. May just need to reset the switch or check its float to see if it is stuck in the up position.
"Cut it twice and it is still too short".
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.