Troubleshooting Ignition Control Board and Ignitor
On my ICP HVAC unit, mod# PGF336080K00A1, I am getting gas flow to the burners but no spark at the electrodes. I am assuming that since the gas valve is opening, that means all the limit and rollout switches are working. I also have power coming out of the pressure switch.
It seems that the round spark ignitor module or the ignition control board is inop. The ignitor module, (#1173831 superseded by #1177395) has four wires going to it. Blue from the gas valve input, green to ground, and the remaining black and yellow wires coming from the ignition control board. Since I don't know what voltages I should be reading from the board, I have no idea which component is bad.
I didn't see any other posts on this. Anybody know if there is a past thread on this or what voltages I should be getting? Or, is it common knowledge as to what component is probably bad?
If the gas valve is 100% getting 24 voltage and gas is getting into the burners with no spark. Then need new spark control board
|All times are GMT -5. The time now is 02:04 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.