Troubles with HVAC
Its a Intertherm furnace with Goodman heat pump/AC
Hunter 44860 thermostat I think this is the problem Change from a old mercury thermostat
Everything is wired correct. 7 wires but blue is caped in the furnace
The are hooked up like
Red R/C R/H jumped Green,G White,W2 Yellow,Y1 Blue,C Orange,O Brown,E
My buddy works for a HVAC company he tested it the first time.
No wires have been changed.
J put in a 3.2A fuse on the blue wire 24v side and that did not stop it.
I just hate to ask for more favors.
Last edited by DestructionDan; 03-02-2011 at 03:06 PM.