||Thread Tools||Display Modes|
|11-03-2008, 09:56 AM||#1|
Join Date: Nov 2008
Posts: 1Rewards Points: 10
Thermostat wiring advice
I am replacing a non-programmable thermostat with a programmable model. I am asking for advice about how to wire the new thermostat. The included instructions are not clear to me and I don’t want to damage anything by connecting it in the wrong way. I have included as much information as I thought was relevant.
My heating/cooling unit is a TRANE XR-13 2TWR3030A1000AA which is a heat pump with emergency heat. I have six wires currently connected to my Totaline thermostat:
Current setup: Totaline thermostat
S1 – no wire
S2 – no wire
O/W2/B – orange wire
R – red wire
C – blue wire
Y/Y2 – yellow wire
Y1 – no wire
G – green wire
W/W1 – white wire
I bought a programmable thermostat with the following connections: Honeywell TH6220D1028
I need help with the yellow, orange and white wires. Here are my specific wiring assumptions and questions:
Red wire from R to R/R
Blue wire from C to C/C
Green wire from G to G/G
Orange wire from O/W2/B to ???? (W2/AUX or W/O\B)
Yellow wire from Y/Y2 to ???? (Y2/E or to Y/Y)
White wire from W/W1 to ???? (W/O\B)
Thank you for your help.
|11-03-2008, 10:33 AM||#2|
Join Date: Sep 2008
Location: Upstate New York
Posts: 368Rewards Points: 250
I'm assuming you've managed to get power to the tstat and actuate the fan so far as you've correctly mapped the R, C and G terminals.
One way to find out is hook up the old stat, break out your volt meter and map out what terminals are energized under each scenario: cool, 1st stage heat, fan only, aux heat, 1st stage w/ aux heat, etc. This may take a while to map out as some heat pump controllers and tstats won't just let you take the system from one mode to another, for example cool to heat, without some built in delay to protect the compressor.
Then hook up the new tstat with just R and C (G if you like) and run it thru these scenarios and see what terminals are active for each scenario.
It couldn't hurt to map out how you're entire system is wired from tstat, air handler to heat pump, so you can fully understand what's going on.
|11-04-2008, 07:04 AM||#3|
An old Tradesmen
Join Date: Oct 2008
Posts: 33,986Rewards Points: 6,928
Red wire to R
Blue to C
Green to G
Orange to W/O,B
Yellow to Y
White to W2
Make a jumper wire, and install it from E to W2/aux.
|heatpump , thermostat , wiring|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Honeywell Thermostat Wiring Differences||DavidHwang||HVAC||16||01-28-2012 02:11 PM|
|Wiring help - Honeywell Thermostat w/ Carrier Heat Pump||Tom Williams||HVAC||7||09-14-2008 07:40 AM|
|Which diagram to use on Lenox Thermostat wiring setup? Heat Pump Lenox techs needed||twilightcall||HVAC||1||08-13-2008 11:49 AM|
|Thermostat Wiring Problem||crazy woman||HVAC||2||08-15-2006 09:22 AM|