||06-29-2011 12:23 AM
Thermostat/Furnace/ and A/C unit
just attempted to install honeywell 6300 thermostat. connected the G W Y R wires and left the blue alone. But now a 24 code is flashing on the furnace. And the thermostat isn't working. Any suggestions?
check the error code legends on the back of one of the doors. code 24 on a carrier may mean blown fuse on the circuit board and improper or shorted wiring. did you have a problem B4 changing the tstat?
||06-29-2011 06:45 AM
verify on the install info if you need the C connection off the furnace transformer at the subbase...if the stat is lit with no action calling stuff in it needs the C
|All times are GMT -5. The time now is 09:08 PM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
Search Engine Friendly URLs by vBSEO