We have a Honeywell Chromotherm III Model T8600A thermostat. Where the temperature should be there are instead the lettser "AC". The furnace won't come on. ANy advice will be appreciated.
That means that your thermostat is not getting 24 volt ac power from the furnace, and is running off it's battery or capacitor only.
This can mean that your 24 volt fuse is blown in the furnace, the 24 volt transformer has failed, or the entire furnace does not have power for some reason.
Pull the thermostat off the subbase, let it set on the table for about thirty minutes. Reinstall the thermostat and see if it works again. The Honeywell digitals are very sucebtible to static shock, if you touched thermostat with and static dicharged into it this will happen. Letting it bleed down removes the malfunction. If it does not work after bleeding it down you will have to replace it.
|All times are GMT -5. The time now is 07:16 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.