Ruud Furnace fan won't turn on
The pilot light starts and the furnance gets hot, but the fan won't turn on. There is a whiring noise like it is trying to start. Is this something I can fix myself? It needs to be fairly easy or have specific directions. We can't get a repairman until late tomorrow and it is cold. Model UGUJ-03NA-CR. There was a small burning smell the other night, like wires burning. It could have been the furnace??? Thanks! Suzy
||02-04-2008 05:36 PM
The capacitor for the blower motor is either dead or you have a dead spot on the armature. If you are careful you could spin the fan by hand and then turn on the power while it's spinning to get it started, then leave the fan switch on the thermostat on to keep it running til you get service.
|All times are GMT -5. The time now is 04:08 AM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.