Replacing an Air Exchange with a Heat Pump?
I my basement I have a rather large Air Exchange http://imgur.com/7ODDFHf. I have heard that if I install a heat pump, I may be able to replace the air exchange. This gives me two benefits that I can see:
1. The Heat Pump will be outside. Giving me more space in my cramped basement.
2. The Heat Pump will lower the temperature a bit in the house durring summer (I have no airconditioning).
However, there are a few things that I'm not sure of:
Thanks for any help!
your unit is actually called an "air to air heat exchanger" or "heat recovery ventilator" Google that.
it is meant to bring in fresh air in the winter which is dry and to exhaust moist stinky stale air. the dry air will remove moisture and the fresh air is good for your health and the other reasons. you do not want to get rid of it unless you don't want fresh healthy air OR you have no humidity issues. some people run them year round on low speed to get fresh air all the time. if you get rid of it your windows may sweat and get moldy so I would not do it.
heat pumps have to be installed inside/on top of a furnace or air handler which is the same idea w/o burners. a box with a fan basically and may have small booster elec elements. you cannot reuse the vents from the exchanger as they are too small /not enough of them and in the wrong places. you would need ducts that look like the ones in a regular house with a furnace which you have seen. also needs return air ducts.
Google Lifebreath HRV or Lifebreath heat recovery ventilator for good info.
Do you have an oil furnace o a boiler? A heat pump could be added to a furnace. A boiler would require an air handler,supply and return duct and the heat pump.
|All times are GMT -5. The time now is 01:36 PM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved