||07-14-2010 04:50 AM
recharging heat pump compressor
i installed a new compressor on a heat pump package unit, and would like to know the correct way to charge it apon start up ?
||07-14-2010 06:12 AM
After a leak check and vacuum pump to 500 microns weigh in the charge. Hopefully you replaced the biflow drier when the system was open.
||07-14-2010 06:18 AM
By weight. The data lavel of the package unit, should have its operating charge on it.
|All times are GMT -5. The time now is 09:03 PM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
Search Engine Friendly URLs by vBSEO