need some help just installed a new
gmh950904cx two stage goodman furnace
gsx130361 3 ton 13 seer ac unit
need help for the right programmable thermostat
for the equipment to run the best it can right now
i have a whiterogers 80 series 1f80-361 single stage programmable thermostat
thanks all dan
While it is a 2 stage Furnace it only uses a single stage stat due to goodman's "Dual Saver technology". Too bad you did not opt for the true 2 stage system with the variable speed blower to have total control of the 2 stage heating from the stat. The stat you have will work well with the system.
Its still a true 2 stage.
It simply is not controllable by a 2 stage thermostat to get the best comfort possible from a 2 stage furnace.
|All times are GMT -5. The time now is 07:06 PM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved