Is there a way to test the pressure switch to see if it is bad?
Bryant 383K gas furnace.
Printed on the switch is the pressure it closes/opens. You need to install a tee fitting in the line to the switch and connect a manometer or magnahelic to the tee. Turn off the fuel to the unit. Then turn on the unit and read the pressure on the gauge. If it makes the printed units the switch should change state when read with an ohm meter.
If not, the switch is bad. Remember, there is a positive and negative side to all pressure switches.
|All times are GMT -5. The time now is 10:33 AM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.