Nordyne G6TL Furnace Question
I recently replaced the inducer blower assembly in a Nordyne G6TL 90+ variable speed furnace.
The new assembly has a condensate drain where the original had none. It appears that a small amount of condensate can end up in the blower housing and they decided it needs somewhere to go.
Can I tap this into my existing condensate drain using the same clear vinyl hose and a tee or does it require something more complicated?
Any thoughts would be appreciated.
Last edited by kentcasey; 01-28-2009 at 10:54 PM.