New HVAC evaporator unit
I have a Ruud Outside Condensing unit and we are replacing the old evaporator unit inside to a Goodman unit with aux heat strips.
With these being two different units the wiring is completely different i was wondering if anyone at all could help me figure out how to wire these two and then to my thermostat
Wiring on the Ruud
Wiring on the Goodman
Terminals on the Thermostat
if anyone had any kind of insight or knew of a way to figure this out please help
model numbers would be very helpful or pictures of schematics or pdf files of the installation manuals.
Outdoor heat pump
Indoor Evaporator Unit
Heat Pump is
UPKA-018JAZ Heat Pump
HP = AHU = Thermostat
---- = RED = R
YELLOW = ---- = Y
BROWN = BLUE = C
PURPLE = WHITE & BROWN = E & AUX
BLUE = ---- = B
---- = GREEN = G
thanks alot i'm going to try this when i get off of work and i'll reply back to let you know if everything worked like it was supppose to again thanks a lot
|All times are GMT -5. The time now is 09:11 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.