my ruud furnace is not working
it needed a new heating element we put one on it now it is blowing but not hot or even warm air please help btw its electric
could be a number of things, fusable link,bad sequencer, broken element burned wires, improperly wired tstat(if recently replaced).
you need a meter and amprobe to diagnose for each 5kw of heat you will be pulling roughly 20 amps i would normally test with power on so im hesitant to advise you to do that. how did you determine you needed an element in the first place?
|All times are GMT -5. The time now is 12:16 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.