my ruud furnace is not working
it needed a new heating element we put one on it now it is blowing but not hot or even warm air please help btw its electric
could be a number of things, fusable link,bad sequencer, broken element burned wires, improperly wired tstat(if recently replaced).
you need a meter and amprobe to diagnose for each 5kw of heat you will be pulling roughly 20 amps i would normally test with power on so im hesitant to advise you to do that. how did you determine you needed an element in the first place?
|All times are GMT -5. The time now is 09:47 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved