Multi stage heat pump thermostat
Hey, I changed out my thermostat on a multi-stage heat pump and it's working fine in heat and E heat mode, but I have question about the 1st and 2nd stage heat. I have not tried the AC mode, but I believe that is on the reversing value (O) and should be fine. My question is: Is Y1 the 1st stage heating and W2 is the 2nd stage heating then Emergency heat is pulled from the 2nd stage with the compressor locked out?
Below is how I have connected my thermostat, but while connecting it I kept thinking the Emergency was 2nd stage.
Thanks in advance. :thumbup:
Old Thermo: Honeywell CT70(Mercury)
W2 - White
G - Green
O - Orange
Y1 - Yellow
New Thermo: Honeywell RTH3100C
C - Blue (Common)
R - Red (Return)
O - Orange (Reverse Valve)
G - Green (Fan)
Y1 - Yellow (1st stage heat?????)
W2 - White (2nd stage heat????)
Emergency - W2 to E connected by Jumper
Yes, you are correct.
Thanks again. :thumbsup:
|All times are GMT -5. The time now is 01:28 AM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.