Luxaire furnace fails to fire
Got a Luxaire(12 yrs old) that once in a while does not light4 times in a month). I tapped on the induction blower and it started. Friend who is in the business says it could be a pressure switch, as they are very sensitive. any thoughts?
sometimes water will get into the tube from the ventor blocking the pressure switch
Try cleaning the tubing
also if you tap on the ventor motor and it starts , it could mean that you have bad bearings
Clarkson Comfort Zone Heating and Air
|All times are GMT -5. The time now is 10:11 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.