inducer blower wont work on my heil gas furence
Which safety and how did you test it? Were the ones you replaced testing bad along with the gas valve or are you randomly throwing parts at it hopeing to stumble across the real issue?
Call for heat from the thermostat will show 24 volts between C and W at the control board. The same 24 volts goes though all the safeties and if they are closed then the circuit board powers the inducer. Check each componet and find out where the problem is and then look into why that safety is open.